NOTE: In July 2016, FERC issued Order 828 revising the Small Generation Interconnection Agreement (SGIA) to require newly interconnecting small generators under 20 MW to ride through abnormal frequency and voltage events and not be disconnected during such events.
Through its Orders 792 and 792-A, the Federal Energy Regulatory Commission (FERC) adopted new "small generator" interconnection standards for distributed energy resources up to 20 megawatts (MW) in capacity in November 2013 and September 2014, respectively. These standards made revisions to those promulgated by FERC in May 2005 through its Order 2006. The FERC's standards apply only to facilities subject to the jurisdiction of the commission; these facilities mostly include those that interconnect at the transmission level. Given that purely intra-state distribution grids are generally considered to not be in "interstate commerce", the FERC's standards generally do not apply to distribution-level interconnection, which is regulated by state public utilities commissions. However, FERC's standard tends to serve as a guidepost for a number of state-level standards.
Small Generator Interconnection Procedures and Agreement (SGIP & SGIA)
The FERC's standards include Small Generator Interconnection Procedures (SGIP) and a Small Generator Interconnection Agreement (SGIA). The SGIP contains the technical procedures that the small generator and utility must follow in the course of connecting the generator with the utility's lines. The SGIA contains the contractual provisions for the interconnection and spells out who pays for improvements to the utility's electric system (if needed to complete the interconnection).
Applicable SGIP/SGIA Interconnection Review Processes
The standards include provisions for three levels of interconnection:
The tables below describes the different "breakpoints," or the various system sizes at which the different processes would apply. The first table is an overall table comparing the breakpoints between the two FERC orders, .
|Standard of Review||Previous Rule
(FERC Order 2006)
(FERC Order 792)
|10 kW Inverter Process||Up to 10 kW||Up to 10 kW|
|Fast-Track Process||10 kW through 2,000 kW (2 MW)||Voltage-Differentiated
(See Table Below)
|Study Process||2 MW through 20 MW||
through 20 MW
|≥ 30 kV and ≤ 69 kV||2 MW||4 MW|
|Applicable Delivery System Voltage Levels |
for Fast Track Process (FERC Order 792)
|Applicable System Size (Regardless of Location)||Applicable System Size (Location-Specific*)|
|< 5 kilovolt (kV)
||500 kW||500 kW|
|≥ 5 kV and < 15 kV
||2 MW||3 MW|
|≥ 15 kV and < 30 kV||3 MW||4 MW|
|≥ 30 kV and ≤ 69 kV||4 MW||5 MW|
Other New Provisions in Order 792 & 792-A (2013 & 2014)
The new rules include other additional provisions intended to promote the efficiency of small generator interconnection, including, but not limited to:
For a detailed look at each and every change to the SGIP/SGIA resulting from Orders 792 & 792-A, please visit FERC's SGIP/SGIA website to view red-lined copies of each.
In July 2016, FERC issued Order 828 revising the Small Generation Interconnection Agreement (SGIA) to require newly interconnecting small generators under 20 MW to ride through abnormal frequency and voltage events and not be disconnected during such events. This ride through requires the small generating facility to stay connected to and be synchronized with the transmission system during system disturbances within a range of over and under frequency/ voltage conditions as comparable to large generating facilities.
|Eligible Renewable/Other Technologies:||
|Applicable Utilities:||FERC standards generally apply to all transmission-level interconnection; state standards generally apply to distribution-level interconnection|
|System Capacity Limit:||20 MW|
|Insurance Requirements:||"Additional liability insurance" required only "if necessary as a function of owning and operating a generating facility"|
|External Disconnect Switch:||Not addressed|
|Net Metering Required:||No|
|Name:||FERC Order No. 2006|
|Name:||FERC Order No. 2006-A|
|Name:||FERC Order No. 2006-B|
|Name:||FERC Order 792|
|Name:||FERC Order 792-A|
|Name:||FERC Order 828 (Frequency and Voltage Ride Through)|
|Name:||Public Information - FERC|
|Organization:||Federal Energy Regulatory Commission|
888 First Street, NE
Washington DC 20426
This information is sourced from DSIRE; the most comprehensive source of information on incentives and policies that support renewables and energy efficiency in the United States. Established in 1995, DSIRE is operated by the N.C. Clean Energy Technology Center at N.C. State University.
Copyright © 2023 EnergyBot • All rights reserved.
1601 Bryan St Suite 900, Dallas, TX 75201